User guide • Read online or download PDF • KYORITSU A User Manual • KYORITSU Tools. Get KYORITSU A User guide. Get all KYORITSU manuals!. Find great deals for Kyoritsu Digital Loop Tester Model A. Shop with confidence on eBay!.
|Published (Last):||26 December 2014|
|PDF File Size:||13.90 Mb|
|ePub File Size:||17.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
Always treat it with the greatest of respect and care.
If you are not quite sure how to proceed, stop and take advice from a qualified person. This instruction manual contains warnings and safety rules which must be observed by the user to ensure safe operation of the instrument and retain it in safe condition.
Therefore, read through these operating instructions before using the instrument. Such metalwork may kyorotsu live for the duration of the test. The cover can be detached and put on the back side of the main body during measurement.
What’s missing? Tell us about it.
Wiring check LEDs The cause of the fault must be investigated and rectified. This mode is cancelled whenever the test button is pressed.
If not, disconnect from the mains and check the wiring at the socket.
In the event of a fault, the Fault loop impedance should be low enough and the Prospective Fault current higher enough in order to have the automatic disconnection of supply by the installed protection device within prescribed time interval. Every circuit must be tested to make sure that the fault loop impedance does not exceed that specified for the over current protection device concerned. The figure below shows in marked line the Fault loop impedance for TN system.
It is fundamental for this example to test also the RCD to ensure that operation takes place quickly kyorutsu to iyoritsu the safety requirements. In order to do it, can be used the RCD tester model A. Rating A 6 10 16 kyoritsk 25 32 40 50 63 80 Disconnecting time 5s Disconnecting time 0.
Max value of Zs for this example is 2. In fact the Zs of 1.
The RCD could trip during the tests also with model A. Failure to follow these instruction can cause hazards to the user. Page 13 In the event of a fault, the Fault loop impedance should be low enough and the Prospective Fault current higher enough in order to have the automatic disconnection of supply by the installed protection device within prescribed time interval.
Page 14 The figure below shows in marked line the Fault loop impedance for TN system.
KYORITSU A : User guide
Page 17 Max value of Zs for this example is 2. Don’t see a manual you are looking for? Tell us what’s missing. Tell us about it. Or point us to the URL where the manual is located.
Your manual failed to upload